Boiler and Auxiliary Technical Services
Industrial fan repairs, replacement, reconditioning and balancing
PO Box 689, Pinetown,
3600, South Africa
+27 31 700 2731
+27 31 700 6684 fax
This assembly was rebuilt after extensive contamination. Leaking bags in a baghouse caused the backward curved impeller to vibrate and destroy parts of the casing and pedestal.
Cost: 30% of new equipment. Atmospheric corrosion of the casing over 12 years rendered OE scrap. The unit was rebuilt with some structural improvements for installation at the wet end of a paper machine.
Click here for our full client list.